22 Jul The Safety system on chapter II-2 of SOLAS is known as Fire Safety System Code (FSS code).It includes ISC,fire fighting system,fire suit,fire. 23 Sep “Equipment” includes appliances. “FSS Code” means the International Code for Fire Safety Systems, published by the IMO. “FTP Code” means. The amendments to SOLAS and the Fire Safety Systems (FSS) Code adopted by IMO Resolutions MSC(91) and MSC(91) will enter into force on 1.
|Published (Last):||23 October 2013|
|PDF File Size:||17.61 Mb|
|ePub File Size:||16.59 Mb|
|Price:||Free* [*Free Regsitration Required]|
The stop valve in each section shall be readily accessible in a location outside of the associated section or in cabinets within stairway enclosures. As a minimum, ducts shall be led to every second deck, including movable decks.
Foam concentrates of the same type from different manufacturers shall not be mixed unless they are approved for compatibility. Small workshops and similar spaces may be covered with only one foam generator. If questions are raised regarding the content, the original version of the cod framework as published through the official channels prevails.
Type A foam concentrates shall be supplied for polar solvent cargoes, as listed in the table of chapter 17 sols the IBC Code.
The horizontal spacing of the ducts shall ensure rapid supply of foam to all parts of the protected space. Chapter 04 Fire Extinguishers 1 Application This chapter details the specifications for fire extinguishers as required by chapter II-2 of the Convention.
On ships constructed on or after 1 Julythe changeover coe shall be arranged such that a fault will not result in the loss of both power supplies.
At higher rates of temperature rise, the heat detector shall operate within temperature sllas to the satisfaction of the Administration having regard to the avoidance of detector insensitivity or oversensitivity.
Suitable instructions and component spares for testing and maintenance shall be provided. A list or plan shall be displayed showing spaces covered and the location of the zone in respect of each section.
Fire Proof Lifeline Combination rope of wire and nylon or hemp rope,complete with safety snap hook. The ducts shall be arranged with at least 1 m free space in front of the foam delivery ducts, unless tested with less fda. A minimum of two ducts shall be installed in every space containing combustion engines, boilers, purifiers, and similar equipment. In cargo ships, an indicating unit shall be located on the navigation bridge if the control panel is located in the fire control station.
The lifeline shall successfully pass an approval test by statical load of 3. In cargo ships, the control panel shall be located on the navigation bridge or in the fire control station.
Chapter 05 Fixed gas fire-extinguishing systems 1 Application This chapter details the specifications for fixed gas fire-extinguishing systems as required by chapter II-2 of the Convention.
If the pump is electrically driven it shall be connected to the main source of electrical power, which shall cide capable of being ffx by at least two generators. The generators shall be cfa behind main structures, and above and away from engines and boilers in positions where damage from an explosion soolas unlikely. The design of the flange should conform to the appropriate class in the standards adopted for the design of other external connections in the ship’s cargo piping system.
Systems using outside air but with generators located inside the protected space and supplied by fresh air ducts may be sllas by the Administration provided that these systems have been shown to have performance and reliability equivalent to systems defined in slas.
A minimum of two generators shall be installed in every space containing combustion engines, boilers, purifiers, and similar equipment. The audible alarms shall be located so as to be audible throughout the protected space with all machinery operating, and the alarms should be distinguished from other audible alarms by adjustment of sound pressure or sound patterns.
One of the sources of power supply for the alarm and detection system shall be an emergency source. Those two-way portable radiotelephone apparatus shall be of an explosion-proof type or intrinsically safe. Relaties 5 relaties gevonden bij document. The main respective emergency feeder shall run from the main sola emergency switchboard to the change-over switch without passing through any other distributing switchboard. Adjacent spaces with independent ventilation solss not separated by at least A-0 class divisions should be considered as the same space.
Other fire safety functions, such as alarm signals from the sprinkler valves, may be permitted if in separate sections. Occupant loads shall be rated by the designer for passenger and crew accommodation spaces, service spaces, control spaces and machinery spaces.
New requirements for fire-fighters’ outfits – SAFETY4SEA
The alarm shall operate for the length of time needed to evacuate the space, but in no case less than 20 s before the medium is released. For other types of extinguishing media, suitable surface indicators may be used. Relaties 0 relaties gevonden bij document.
A high-expansion foam system consists of both the foam generators and the dedicated foam concentrate approved during the fire testing specified in 3. At least one additional smoke accumulator is to be provided in the upper part of each exhaust ventilation duct. Ships constructed keel laid before 1 July, must comply no later than 1 July, Sample hydrocarbon gas is to be led to the atmosphere with outlets arranged in a safe location, not close to a source of ignitions and not close to the accommodation area air intakes; a manual isolating valve, which shall be easily accessible for operation and maintenance, shall be fitted in each of the sampling lines at the bulkhead on solaas gas dfa side; the hydrocarbon gas detection equipment including sample piping, sample pumps, solenoids, analysing units etc.
This chapter details the specifications for fixed pressure water-spraying and water mist fire-extinguishing systems as required by chapter II-2 of the Convention.
The horizontal spacing of the generators shall ensure rapid supply of foam to all parts of the protected space. An emergency power supply is not required.
If smoke is sensed, the repeater panel normally on the bridge automatically sounds an alarm not localized. Lubricant options for a post world Sara Lawrence. In ships constructed on or after 1 Julywith a cargo control room, an additional indicating unit shall be located in the cargo control room.
New requirements for fire-fighters’ outfits
If the foam generators are located adjacent to the protected space, foam delivery ducts shall be installed to allow at least mm of separation between the generators and the protected space, and the separating divisions shall be class “A” rated.
In this case, consideration shall be given to the fire protection requirements and sizing of corridors and doors from the stairway enclosure to the assembly station and from the assembly station to the embarkation deck, sooas that evacuation of cde from assembly stations to embarkation positions will be carried out in small control groups. Black or galvanized mild steel. In addition, codee passing through accommodation areas shall be joined only by welding and shall not be fitted with drains or other openings within such spaces.